- About Us
- Air Conditioners
- Heat Pumps
- Commercial HVAC
- Other Services
- Contact Us
Heating and cooling account for about half of your total at-home energy usage. No wonder you’re on the lookout for energy saving tips! Perhaps you’ve heard that closing air vents in unused rooms saves energy. It seems logical that with the door shut and the vent closed, your HVAC system would be free to heat and cool the rest of your home more efficiently.
Unfortunately, closing vents actually wastes energy. Discover the unintended consequences of closing vents, and you’ll realize how ineffective it is for lowering your utility bills.
Ideally, duct systems should have low air leakage rates. However, even well-designed ductwork isn’t completely leak-proof. And if you close several air vents, the increased pressure within the duct system causes more leaks. This forces air from unconditioned spaces to circulate around your home, reducing the efficiency of your air conditioner and furnace.
The high pressure within the duct system causes variable-speed blower motors to work harder as they attempt to maintain adequate airflow. This defeats your efforts to save energy.
Most HVAC systems have a single-speed blower motor that operates at only two settings: on and off. It can’t combat the high pressure within the duct system, resulting in lower airflow. This means less heated and cooled air circulates around your home, making it less comfortable. Low airflow can also cause the AC evaporator coil to freeze, which makes the air conditioner unable to cool your home.
Low airflow over the AC evaporator coil causes some refrigerant to make it back to the compressor as a liquid, damaging this equipment over time. There’s also a higher chance for a cracked furnace heat exchanger, which requires immediate repair.
If you’re discouraged after learning that closing vents doesn’t save energy, try these other more effective energy saving tips:
For help implementing these and other energy saving tips, please contact Arctic Air Conditioning today.
”have been using arctic air for almost 30 years. excellent company.”
”Great service as usual.”
”I have been using Arctic air conditioning for many years. They are prompt and courteous, and never recommend maintenance that is unnecessary. The new system of text messages and emails…”
”Technician arrived even a couple minutes early and efficiently completed the annual heating check up. I've always had good experiences with this company right from the day they bid on…”
”Javier was simply delightful. Friendly and efficient. He arrived at 9.30 am (I received an email very early morning to say he was on his way. He was supposed to…”
”Price as quoted, arrived on time , courteous technician .”
”Very prompt in schedule arrival. Technicians are knowledgeable, customer focused and very professional.”
”Very professional and reliable. I have been using them for years and am very satisfied.”
”Your technician Kevin was excellent. A credit to your company”
”On time. Cleaned up. Friendly. Great job! Thanks Sammy!”
”I am very happy with service ,Nicole was so helpful went above and beyond to help to fix problem,kind,patient ,knowledgeable compassionate employer, thank you Arctic Air and Nicole! Mariana”
”Arctic air, these guys are prompt in returning calls and they are really good. Special mention to Jesse , an extremely nice gentleman, who changed our water pressure regulator, and…”
”Called Arctic Air at 4:50 yesterday evening after hearing a noise from the furnace. Technician Michael C arrived within an hour and diagnosed the problem. Could not have been more…”
”Knowledgeable Technicians, great service, great price”
”Great service and on time”